Installation of the wood generator
The ECOPOLY 2 complies with French standards. It can therefore be installed directly in a workshop, without a protective cage.
Indeed, thanks to the ventilated double fairing of the exchanger, the outside temperature does not exceed 60°C for a nominal power developed.
The loading door handle has high temperature insulation. The blower grille protects against the thermal production of the exchanger on the facade.
ECOPOLY with duct network
The adaptation piece placed in place of the blowing grille allows the installation of a duct network for additional air distribution to another room (office, shoxroom, store, home, etc.)
In the case of office or home heating, a filtration box on the fan is offered as an option.
To transport hot air to another room (office, store, etc.), it is possible to install a duct network, fitted with connection elements (90° elbow, 45° elbow, tee, reduction , blowing grille…). We carry out air distribution studies on request
ECOPOLY in a boiler room
When you want to isolate the ECOPOLY 2 from the room to be heated, particularly in a boiler room, it is necessary to recover the mass heat produced by installing an additional fan as well as an external control cabinet for regulation management air, safety and protection.
In this case, the air flow is doubled, i.e. 4,000 m3/h for the ECP50.2, 50 kW model and 8,000 m3/h for the ECP100.2, 100 kW model.
Installation for wood dryer
ECOPOLY 2 is installed outside the dryer or container in a closed room with the addition of an auxiliary fan on the dryer partition for fresh air intake + recycling.